Lord Fin tube-Daily inspection of the heat pipe heat exchanger
Daily inspection of the heat pipe heat exchanger
When the temperature of the heat pipe to the gas outlet of the heat exchanger is higher or lower than the standard value, you should check and find out whether there has been the following occur:
1. The high temperature of the exhaust gas inlet temperature has exceeded the allowable value or value drops too low.
2. The high temperature of the exhaust gas flow rate exceeds or insufficient.
3. The low temperature side flow is low or too much?
4. Is there a heat pipe heat exchanger fouling accumulation.
When the case to the gas or exhaust normal, or no ash accumulation, if found a huge change in temperature or temperature efficiency, you should check and find out if the following occurs:
1. The heat pipe heat exchanger is damaged?
2. Is the case of heat pipe heat exchanger exhaust pipe blocked exist?
3. Hot and cold fluid tight seal spacer is damaged, whether produced two fluids blended